We'll help you find the right solution for your needs
Does this sound like your topic?
Case Conclusion Date: 12.01.2011
Practice Area: Defective and dangerous products
Outcome: Settled for Confidential Amount
Description: A boiler service technician sustained severe head, brain and facial injuries in a boiler explosion at a poultry plant in Gainesville, Georgia on January 14, 2008, The plaintiff was an employee of a boiler service company who was sent to switch fuel supply for the boiler from gas over to fuel oil. The boiler supplied steam for the plant, and they wanted to maintain pressure while the change over to oil took place. Investigation of the explosion by the Georgia Department of Labor determined that the oil supply and return lines had been reversed, causing an excessive accumulation of fuel in the hot boiler as Mr. Beck attempted to fire the burner on oil. The burner had not been fired on oil since a new boiler was installed two years before. Plaintiff contended that the lines had been reversed when the new boiler was installed by another boiler service company, and that the manufacturer of the burner had supplied a defective manifold making it possible to inadvertently reverse the lines at the point of attachment to the burner. The boiler inspection company which had last inspected the boiler prior to the explosion was also named as a defendant.